11kv XLPE Insulated Power Cables
|FOB Price:||US $7.5-85.2 / Meter|
|Min. Order:||300 Meters|
|Min. Order||FOB Price|
|300 Meters||US $7.5-85.2/ Meter|
|Production Capacity:||500,000 Kilometers Per Month|
|Payment Terms:||L/C, T/T|
- Model NO.: yjv
- Voltage: Low and Medium Voltage Cable
- Insulation Material: XLPE
- Insulation: XLPE
- Armoured Layer: Copper Tape
- Transport Package: Drum or According to U Request
- Origin: Zhengzhou, Henan, China
- Application: Power Station
- Current: AC Cable
- Certification: ISO
- Sheath: PVC
- Trademark: Yifang cable
- Specification: 1*4~5*630mm2
- HS Code: 8544460120
Customer Question & Answer (0)
The products are mainly complying with iec 60502 standard, also can be produced according to OEM requirements and other standards, such as bs standard, DIN standard, ASTM standard, etc.
Voltage grade is up to 35kv, cross-section area can be up to 1000 sqmm (copper or aluminiun conductor). Conductor long-time operating temperature is 90 degrees. In short circuit, conductor highest temperature should be not more than 250 degrees.
Laying conditions: For lyaing under ground with large different altitude, be able to bear external machanical force and moderate pulling force.
1kv-35 kv multi-cores/ copper or aluminium conductor/ XLPE insulation / copper tape or copper wire screen / galvanized steel wire armored / PVC or PE sheath / power cable,
High voltage (35kv~220kv) copper or aluminium conductor/ XLPE insulation/ metal sheath (lead or corrugated aluminium)/ HDPE or PVC outer sheath power cable.
The products are strictly complying with iec 60840 standards, also can be produced according to reasonable OEM requirements and other standards, such as bs standards, DIN standards, ASTM standards, etc.
Long time operating temperature for cable conductor is 90 degrees.
The highest temperature of the conductor in short circuit (no longer than 5 seconds) in not more than 250 degrees, if a joint is in the cable, the temperature of the tinning welding joint is not more than 120 degrees, compressing joint not more than 150 degrees and electro-welding joint not more than 250 degrees.
No drop in limited provided there is full mechanical tention when cable is laid. It si forbidden to lay cable in iron-pipe or to fix cable by circling around the cable with iron materials.
Being laid, the minimum temperature of the cable shall not be lower than zero degree. In the case of lower temperature, heating measures shall be taken.
-How do you ship the products?
-What is the warranty for the product?